It is installed at the output end of the inverter, which is used to limit the capacitive charging current of the inverter and the motor connecting cable, and inactivate the voltage rise rate of PWM wave output by the inverter. When the length of motor cable exceeds a certain value, it is recommended to insert a motor reactor between the inverter and the motor, which is used to compensate the recharging current of capacitor in case of the long wires. The maximum length depends on the rated value of the frequency converter and the type of the motor cable.
The input reactor can be used to provide improved overload protection for the line power supply, and to reduce the current harmonic distortion produced by the inverter. Increase the power factor of input power supply, reduce the high harmonic, and restrain the surge of frequency converter in the power supply equipment
The SG series three-phase dry-type isolation transformer is a new generation of energy-saving dry-type transformers developed and produced by our company on the basis of reference to similar international products and combined with applications. From...
DC Smoothing Reactor
DC smoothing reactor is used in the rectifying circuit to restrain the ripple pulse component after rectification and make the rectified current continuous, so as to improve the output branch waveform and guarantee the normal operation of DC equipment. The smoothing reactor is used as the series reactor in DC machine supplied by the converter, in order to eliminate the DC link in the current and voltage DC link converter; It is supposed to decouple the converter components on DC side. The power converter on DC side has high pulse circuit feedback to reduce the difference value limit, so as to limit the ring current on the connection with ring current, at the same time, limit the the rising rate of current. The smoothing reactor adopts the iron core of TEM and TET or TPK air core reactor, depending on the requirements on electromagnetic induction.
Sine wave filter
Reference / lmplementing Standards: IEEE519(EN61000-5-2) Electromagnetic compatibility (EMC) EN 61558-2-20(VDE507-2-20) Safety of power supply equipment and similar equipment GB 145493-93 Power quality, utility grid harmonics
Reference / Implementing Standards: IEC60076-6:2007 Reactor GB1094.6-2011 Reactor (eqvIEC289:1987) JB9644-1999 Semiconductor electric drive reactor
Energy Feedback Reactor
Reference / Implementing Standards GB1094.6-2011 Electric transformer JB9644-1999 Semiconductor electric drive reactor IEEE519 - 1992/EN6100-5-2
Reference/ lmplementing Standards IEEE519(EN - 2-5) Electromagnetic Magnetic Compatibility(EMC) EN61558-2-20 (VDE 507-2-20) Safety of Power Supply Equipment and Similar Equipment GB145493-93 Power Quality Public Power Grid Harmonic Wave